Sunday, October 19, 2014
This pic is from a sewer job on Long Island, New York earlier in this month.(Picture is upside down) Customer's house was remodeled and moved back into 6 months ago. Was having repeated problems in the branch line for the last 4 months. Called us out for a sewer cleaning service and a sewer camera inspection to further evaluate. We found pieces of cast iron pipe catching waste and paper. Customer then remembered a toilet flange that was replaced and raised to accommodate a new tile floor. End result was a sewer jetting of the sewer branch to remove a total of 10 good sized pieces of pipe. Customer viewed camera after sewer jetting and was very pleased. Sewer line completely cleaned. Job was guaranteed for 1 year.